Lower Cyanuric Acid Levels Without Draining?
Lower Cyanuric Acid Levels, Video by Andrea Nannini of Hibiscus Pool & Spa
Okay, so maybe I released this information before it has been deemed a proven method of reducing Cyanuric Acid levels chemically. This was a conscious decision, not something that I just blurted out on the spur of the moment. It’s not a statement that I wish I could retract. I have been experimenting with Aluminum Sulfateas a means to Lower Cyanuric Acid Levels (C₃H₃N₃O₃).
The Great CyA Debate in it’s Entirety Below ⬇
As I stated at the CyA debate at the IPSPE in New Orleans, I have had some success. I wanted to share that information because I do think it is something to get excited about. Maybe not bouncing off the walls with joy excitement, but a least a little enthusiasm toward the results.
Why announce it now?
To fully comprehend the reason you must first understand that all of the research I conduct is with the goal of making the industry better. I’m not looking to capitalize on my findings. I’m not funded, nor am I paid. Everything I do and has done has been 100% out of pocket.
So why do it at all?
There are a lot of questions out there that we don’t have actual answers to. I mean, it’s 2019, right? Maybe there is something that was missed, or not yet considered. Take a look at the Black Algae research I conducted last year. I uncovered and had proven quite a bit of information that had been unknown up to that point. If we can come up with a low-cost means of lowering CyA without the need for RO or water replacement, this will certainly benefit the individuals that employ these methods.
To View, our findings on Black Algae, visit us at Black Algae Myth BUSTED
What made you think Aluminum Sulfate could be a solution?
I know adding melamine to the water will pull Cyanuric acid out of solution, but melamine is an extremely expensive material. At a 1:1 ratio with CyA (it takes one pound of melamine to pull one pound of Cyanuric acid out of solution) implementing this procedure would be a costly venture.
I have used alum for many things over the years. Everything from removing Copper Stains from plaster to green to cleans on REO properties (foreclosed homes), but I had never thought to conduct a before and after Cyanuric acid test until 2019.
Lower Cyanuric Acid Levels
Aluminum Sulfate Al₂(SO₄)₃ is the active ingredient in those two-pound cylindrical containers marketed as “Floc” that you see. The dose rate you typically find on those containers will only treat cloudy water at best. To utilize the chemical to its full potential, you’ll need to follow water treatment center guidelines at least as far as dose. Alum, those who have worked with the product, is also temperamental with particular pH and temperature requirements. The water needs to be at least 70°F or better. If the pH is too low, it will not work if the pH is too high, it will not work.
What’s the Best pH for Floc?
Even under normal circumstances, the question of the correct pH to use is controversial. Precedence and Water treatment facility use dictates a pH between 6.5 and 7.2 for best results. The instructions on those two-pound containers we spoke of a moment ago generally call for a pH of 8.0 or higher. Truth is, as you can see in the chart below, Alum will work well within a pH range of 5.8 to 8.0 with a teensy bit of leeway on either end.
There is a difference, though. From other experiments I have conducted I have found that it takes about twice the amount of alum to achieve a result at a pH of 8.0 than it does at 7.0
My initial thought noting the decrease in solubility of solids at a high pH was to go high. I conducted my tests in a range of 7.8 up and through 9.0, well into the field where anionic aluminate becomes dominant. I did so with a water temp of 75°F and doses of aluminum sulfate ranging from 25 ppm through 100 ppm. My results, at best, were minimal.
Lower Cyanuric Acid Levels
Alum is Al2(SO4)3, when put in water it splits into Al+3 (aluminum) ions and SO42- (sulfate) ions. Water is H2O. It can split into H+ (hydrogen) ions and OH- (hydroxide) ions. The aluminum ions can combine with the hydroxide ions to form insoluble floc which is Al(OH)3. Since alum is taking out the hydroxide ions, we are left with a surplus of H+ ions. pH = -log[H+], so pH is a measure of the hydrogen ion concentration. When the number of hydrogen ions goes up, the pH goes down. When the number of hydrogen ions goes down, the pH goes up. That means that when you add alum and get a surplus of H+ ions, the pH will go down.
Back to the drawing board
Okay, not the results I wanted, but I did have results. Besides, that was still somewhat exciting. I decided that I would go back to my usual MO for Alum and ride the pH low. I would repeat my experiment with my pH in a range between 6.0 and 7.2, the other parameters would remain the same.
Here is What Has Worked Best So Far
Water Temp: 75°F Ideal (70°F – 90°F)
Alum Dose: 100ppm (8.33 lbs per 10K gallons)
All other Values (TA, CH, TDS) were within the recommended ranges.
With that, I have achieved a reduction of Cyanuric Acid from starting levels of 90 to 100 ppm by 50%. There is still much more testing to be done, and at this point, I am uncertain if I had achieved a 50% drop, or merely a 50ppm drop due to my start point. The time required to make the noted change was twelve to fourteen hours. Circulate bypassing media following dose then stagnant twelve hours before an extremely slow vac to waste.
Though positive results have been achieved, this experiment is still in its infancy and is far from being considered as proven. Honestly, I think it needs to be successful hundreds, if not thousands of times before I would say it’s a success. This is where feedback from others, before and after CyA levels, that floc with alum in high doses would be beneficial.
I know the dose rate of 8.33 pounds per 10,000 gallons sounds expensive, and if you are purchasing those two-pound bottles of “Floc”, it will be. Alum is available for water treatment centers in fifty-pound bags and at the cost of somewhere between $25 and $35 each and can be purchased through swimming pool distribution centers.
Do Not Try This At Home!
This is clearly only a process that should be attempted by a Swimming Pool Professional. You’ll need to be well versed in the EXACT method of adding a dose of alum to include filter run time, attention to pH level, precautionary measures for filter equipment, and you’ll need to be prepared to slowly vacuum a massive amount of “sludge” from the pool floor with a portable vac system (Not a Hammerhead or Riptide style vac).
Please keep in mind there is still much tweaking (not twerking, that’s Cyrus, not CyA) to be done. If you are a Pool Professional and utilize alum in a high dose, I would greatly appreciate it if you shared your before and after CyA results. This is how we go from my statement of “some success” to a proven method. Please let us know in the comments below.
Here’s why this would be great
Alum is extremely inexpensive and easily obtainable. It may take some convincing to get your distributor to supply product in a bulk size, but it is definitely available to them. Even on the high end at let’s say $35 per fifty-pound bag, that works out to $0.70 per pound. At a dose of 8.33 pounds per 10K gallons, the total cost of chemical (outside pH adjusters) would be $5.83
A thought on why this is working
Since CYA can lose three protons, just from a charge balance point of view, you would think it might be able to form 1:1, 1:2 or 1:3 complexes with Al+3 depending on the pH. The CYA species in a pH 6-8 range, you will have mostly H3CYA, which I would not expect to bind Al3+, and H2CYA-, which has a negative charge and so might be expected to bind to something positively charged, like Al+3. You might expect then that the 1:3 ratio and write the formula as Al(C3N3O3H2)3. Of course this is all purely conjecture.
NOTE: Aluminum sulfate or any sulfate product should not be used in a saltwater pool as at high levels it may shorten the life of the salt cell (Manufacturers do not provide information on concentration). High sulfate levels (> 300 ppm) can cause damage to stonework. Aluminum sulfate should not be used in a pool with pigmented (colored) plaster as some have reported bleaching to occur. A swimming pool should be tested for residual aluminum following use and EPA Secondary Contaminant Aluminum max level of < 0.2 ppm maintained
I hope this and other research I have conducted serves to encourage others to buck the status quo. Continually think Outside the Pool!